Underfloor heating has become increasingly popular in both Retail and Commercial use. The claimed advantages of energy efficiency combined with this obviously comfortable heat source means it is being specified for many new homes particularly in the self-build sector and in many commercial developments
Suitability of Brintons carpets
Brintons carpets are suitable for use with underfloor heating systems at the normal operating temperature of 270C, it must however be appreciated that all carpets and tiles act as thermal insulation materials and this means that carpeted floor takes slightly longer to get warm initially, but stays warm longer. The choice of underlay and installation system is also critical for best performance from the heating system. Carpets and underlays resist the transfer of heat to a lesser or greater degree and this "thermal resistance value" can be measured as a "tog" value. Please see Guidelines for Installation of Carpets and Underlay and tog values for Brintons carpets further down this page.
Confirmed suitability testing of carpets
Recent tests carried out jointly by the UHMA (Underfloor Heating Manufacturers Association) and the Carpet Foundation have confirmed that carpets perform better than had been expected with underfloor heating. Previous combined tog values for carpet and underlay tested under the 2 plate method have been shown to be higher than the tog value obtained when tested in an actual room set condition with carpet open to the surrounding air. The combined tog value of carpet and underlays obtained when tested under the 2-plate system can be lowered by as much as 1 tog to give a more meaningful result.
We always stress to our customers the need to give the information on tog values for their choice of underlay and carpet to the heating manufacturer to ensure that the heating system can perform correctly.
Types of underfloor heating systems
There are a variety of underfloor systems available and the manufacturers tend to recommend different maximum tog values
Water pipes buried in screed
With an underfloor system which uses water pipes buried in screed the maximum acceptable combined tog value of the carpet and underlay is often given as 2.5 tog or even higher. Brintons carpets are generally suitable for use over this type of system (We always recommend that you consult with the heating manufacturer to ensure that the carpet/underlay combined tog value is suitable for the system)
Electric heating cables buried in screed or within a suspended timber floor
These systems have a greater tendency to overheat with thicker floor coverings and for this reason a maximum tog value of 1.5 may have to be adhered to. (We always recommend that you consult with the heating manufacturer to ensure that the carpet/underlay combined tog value is suitable for the system)
Electric heating mats set on top of a structural floor
These products are generally only recommended for use under tiled or other hard floors. If however carpet/underlay is installed then suppliers of these types of matting would generally recommend that they should be covered by a flexible adhesive/levelling compound before any floor coverings are laid. This is to prevent the underlay/carpet moulding itself to the levels of the shape of cables in the matting so that they can be seen in the carpet. The maximum tog value quoted by the system manufacturer should be adhered to (We always recommend that you consult with the heating manufacturer to ensure that the carpet/underlay combined tog value is suitable for the system)
Guidelines for Installation of Carpets and Underlay
As a general rule doublestick installation systems are recommended to provide close contact between the floor, underlay and carpet allowing better heat transfer and to avoid uneven heating pockets.
Tog Values of Brintons Carpet
Typical Brintons 80%/20% wool/nylon carpets have Tog value between 1.0 and 2.2. We can offer the following information, which has been taken from test reports in accordance with BS 4745 two-plate test from BTTG Shirley, Manchester. *Actual copies of these reports are available on request. Click here for information of Tog ratings
Choice of underlay
There is a balance to be sought in the choice of underlay. The underlay used should allow adequate heat to pass through the floor covering into the room space above whilst also giving the carpet adequate support to enhance the carpet's performance over it lifetime.
Thermal Resistance values of Underlays
The thermal resistance of underlay is dependant on a number of factors the most important being what it is made of and its thickness. Felt, which is not normally recommended, has a greater thermal resistance than crumb rubber. Generally thinner rubber products perform best. Tog values of underlays vary considerably. Typical Tog values for felt underlays (which are not normally suitable) would be in the order of 2.5 to 2.9 togs. System Ten (Duralay) has a value of 1.55 Togs, but is generally considered to be too thick to perform satisfactorily with underfloor heating.
Durafit (Duralay) is 1.09.
Roma and Silver Lining (Ball & Young) have values of 0.8 and 1.5 Togs respectively,
Duralay have recently introduced a new range of underlays specifically designed for underfloor heating called Heatflow, for domestic and commercial use. The Tog values are 0.75 and 0.92. The 0.75 tog domestic product is for stretch installation and the 0.92 tog product is for stretch or double stick installations.
Two of our preferred underlays both from the point of view of carpet performance and for low tog values are Gates Technics 5 (tog value of 0.5) and Technics 6 (tog value 0.63). Both are doublestick underlays.
Normal tackifiers and adhesives such as F Ball F41 & F3, are suitable for use at the normal average surface operating temperature of 290C. However, it is important to ensure that the heating is switched off for 48 hours prior to installation and for 48 hours afterwards. In addition, after installation, the heating should be brought up to full working temperature over a period of 7 days.
Where the carpet is due to be laid on a wooden subfloor it is very important to ensure that adequate time has been allowed for the wood to condition whilst the underfloor heating is running to avoid variability in dimension from changes in moisture levels. Brintons cannot be help responsible for ruckling or shrinkage of carpet and underlay caused by movement in the underlying floor surface.
This information is given as a service to our customers only. Suppliers of the flooring timbers, underlays and adhesives together with the underfloor heating manufacturer should be made aware of the combined tog values of the carpet/underlay so that the correct settings and calculations can be used.
© copyright Brintons 2006
Brintons Web Site